Description Two, three or four copper conductors with low temperature insulation (RW90 XLPE) and bare copper bonding wire. Conductor assembly paper wrapped and covered with bare interlocked aluminum armour. Rated 600 volts.
Temperature -40°C to +90°C
Approvals CSA Spec C22.2 No. 51-M89
Application For open and concealed wiring in dry locations only. For use in cable troughs and ventilated flexible cableways in dry locations only. Minimum recommended installation temperature minus 40°C (with suitable handling procedures). Maximum conductor temperature 90°C. Approved for use with ceiling fixtures.
**Copper bonding wire supplied with copper conductors. Aluminum bonding wire supplied with aluminum conductors.
Colour Code: 2C – Black, White 3C – Black, White, Red 4C – Black, Red, Blue, White. #For 3-wire 120/240 and 120/208V residential services or sub-services, the allowable ampacity for sizes #6, #2 and #4/0 AWG aluminum shall be 60, 100 and 200 amperes respectively. #2/0 AWG copper shall be 200 amperes. In these cases, the 5% adjustment per C.E. Code Rule 8-106(1) cannot be applied. Assuming 4th conductor is the neutral of a balanced 3 phase 4 wire system.